The description "G" stands for grease separator basic version. The version corresponds to the requirements according to EN 1825 and DIN 4040-100.
The grease separator has to be opened for emptying and cleaning. Extraction and rinsing of the grease separator takes place manually from the disposal vehicle. Cleaning and rinsing are preferably carried out using hot water through the servicing opening.
The grease separator for underground installation should be installed outside the building as close to the drains as possible. If necessary, the inlet connection pipes to the grease separator should be routed heat-insulated or heated. The necessary frost-free installation depth is achieved using telescopic upper sections which allow adaptation to the inlet and outlet pipe (sewer). The covers for the load classes A/B and D are screwed odour-tight and correspond to EN 124.
The grease separator system "G" for underground installation is usually installed where odour pollution during disposal are not important in the direct vicinity. It has to be possible for the disposal vehicle to drive up to the separator.